Very good experience, high knowledge of products and services. Overall great experience. And would recommend to anyone
Did a great job explaining my options, ordering and installing my air conditioner, in a very timely manner. Communication from start to finish was accurate and informative, very helpful in understanding my options. Air conditioner was installed and is working properly. A few years back you installed my furnace, very happy with both installations. Thank you!
Dan was our technician, and I can't say enough good things about him! He is so personable, and did a great job. He explained things well, and worked hard to make sure I knew what all my options were. He also went out of his way to have me talk to another member of the Black Haak company to see if replacing my furnace would be a better option. Dan understood when we couldn't afford that right now, and didn't push us to go beyond our budget. He was a really great guy!
12/7/18. Removed old furnace. Installed new temp star furnace. Connected new metal on top to attach furnace to duct work. Reconnected the electrical and thermostat wires. Hooked the venting back up to furnace. Ran new drain line from coil and furnace to drain hose that was going through wall. Hooked the gas back up to the furnace. Started furnace and it is running and draining as it should. Thank you for choosing Black-Haak for your heating needs.
No heat at the time I arrived. Cycled system. System would not light up due to obstruction in venting. Tryed to check intake venting with camera, could not find obstruction. Removed intake venting and vented intake to basement. System fired as normal. Checked heat exchanger, found it very rusted and damaged. Cracks starting to form. Ventor motor bearings are very worn. Igniter is in very poor condition. Burners are very rusted and damaged. System is in very poor shape. Checked CO and XS air in exhaust. XS air is high at 198. Clogging secondary heat exchanger.
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time. The customer would like a call in the spring for a possible air conditioning cleaning.
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time.
Performed furnace clean and tune; started by inspecting the exhaust and intake pvc ensuring all connections were secured, I then removed and cleaned burners along with the flame sensor, I then cycled the system on and checked gas pressures did find second stage not engaging after investigating did find the Tstat being a single stage Tstat, I replaced this Tstat with a T6 I cycled the sytem on and got second stage to engage, lastly I performed a combustion test verifying no CO in the airstream. Job complete
Ran new wires to dryer and stove. Replaced dryer and stove receptacle with new 4 prong receptacles and replaced the appliance whips on both appliances. Installed (2) new pendant light over the breakfast nook.
Performed level 2 Package Cleaning. Furnace. Ventor motor bearings are showings signs of wear. Heat exchanger is a little worn with rust. Burners and flame sensor are cleaned off, but showing signs of wear. Combustion analysis test was normal. No CO in the airstream. Found rust in both furnace compartments. Rust came from a loss exhaust fitting that was leaking water. I tightened the fitting and there is no leaks or standing water at this time. AC. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is clean. Refrigerant charge was good. Temp split was 17 degrees. HVAC system is operating normal at this time.
Was here for a air conditioner cleaning. Performed preferred customer air conditioning cleaning. Completed air conditioning cleaning form. Checked the indoor coil for leaks. Didnâ€™t find a leak. Checked the electrical. Found a worn compressor contactor and a worn capacitor. Recommended replacing. Customer has opted to replace the parts himself. Refrigerant levels are ok. Air conditioner is running at this time.
No cool. Condenser wasnâ€™t running. Found the breaker was turned off for air conditioner, rest the breaker. Checked charge, it was really high. The condenser was dirty. I washed it out and checked the charge. The charge is good. The temperature drop in the house i at 18 which is good. Air conditioner is cooling. Office will call to schedule clean and tune.
I completed a level 2 preferred customer cleaning on the tempstar A/C. I used coil cleaner on the outdoor unit and checked all of the electrical components, everything is good. The refrigerant charge looks good. The filter needs to be changed, the 20X25X4 filter that is in now is very dirty and will cause issues with the system if left. The office will follow up to see if we should get a filter.
Performed pkg clean and tune as well as a safety check in the mini split system. Checked wiring and electrical on the AC. Tested compressor, ok. Checked capacitor and contactor, ok at this time. Cleaned coil. Hooked up gauges to system and checked temps and pressures, ok. Subcooloing was 10. Super heat was 11. Split was 20. Compressor is very loud and has some knocking to it. Will continue to monitor to ensure operation. Also, major vibrations from condenser fan motor. Mini split. Cleaned coil, checked electrical system, ok. Checked cooling. Temp was 42 on evap coil. System operating normal at this time. Furnace. Cycled system. Blower is very loud. Bearing ware on ventor and blower motor. Found some water damage in burner compartment. Cleaned system. Checked heat exchanger. Tested for CO in airstream, none. Normal CO and XS air in exhaust. Both the AC and furnace have signs of ware. Average life of these systems are 14 years. Job completed. Office to bill for service.
AC clean and tune. Checked electrical compartment. Cleaned condenser. Cycled system. Hooked up gauges and tested pressures and temps, ok. No indoor or outdoor load. Super heat was 14 and split was 15. System operating normal at this time. Job completed.
Performed furnace clean and tune. The furnace is operating properly at this time.
The water heat was on ignition/flame failure fault. I reset the control and it fired up and ran normally. I removed the burner and igniter/flame sensor assembly and cleaned up the flame sensor had some buildup on it. I took an Ohm reading on the igniter and found 16.9 ohms, manufacturer recommends it get replaced as it gets closer to 18.8 ohms. If problem continues we will need to replace the igniter. Miscellaneous task is for removing the burner and cleaning the water heater flame sensor. Anthony Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time.
Performed level 2 furnace c+t. Igniter and flame sensor showing signs of wear. No CO in airstream. System operating normal at this time. Installed water panel and 2210 electrostatic filter. AW.office to schedule ac clean and tune. Paid.
Installed a new furnace.
Gas Furnace cleaning
Heating and Cooling
We are here to serve your Fox Valley home or business!
Copyright © 2018 | Black-Haak Heating, Inc | All Rights Reserved