Performed furnace start up; inspected the exhaust and intake PVC ensuring all connections were secured, sniffed the gas line for possible leaks, cycled the system on and checked gas pressure, as well as performed a combustion test verifying no CO in the airstream, and lastly replaced the 16x25x1 filter. This system is currently operating normal and heating at 45 degrees at this time. Job complete
Installed aprilaire system. Cut in unit and bypass. Cut in and wired control. Wired up unit to furnace terminal strip. Wired outdoor sensor, piped water to unit. Ran drain line. Cycled system. Operating normal at this time. First year furnace clean and tune. Cycled system. Checked heat exchanger. Checked and cleaned burners and flame sensor. Checked igniter, ok. Checked and adjusted gas pressures to maximize efficiency. Checked for XS air and CO in exhaust, normal levels found. No CO in airstream. System operating normal at this time. Installed 16x25x1 electronic air cleaner. Job complete.
Performed gas furnace start up. All registers are in. Duct work is sealed. No gas leaks detected. No CO in airstream. Temp split was 45 degrees. Unit is running normal at this time. Job complete.
We are here to serve your Fox Valley home or business!Scedule a Service Today!
Copyright © 2019 | Black-Haak Heating, Inc | All Rights Reserved