Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Gary was timely, professional and very customer oriented.
Excellent open discussion of the status of the AC unit relative to age. Talked about options for replacement and timeline based on motor ohms and expected life. He was personable, worked thoroughly & was very knowledgable.
I was very pleased with all aspects of the service I received.
Hunter was on time, friendly and answered all the questions that I had an out our furnace.
Replaced both capacitors in the geos and cycled them. Geos started up and no other problems found. Both geos are operating properly at this time. Thanks Brad
Prefom 2 geothermal clean and tunes and one first year boiler clean and tune. Replace two air filters and 2 water panels. Clean out the drains and test the performance of each unit. Fix venting leak on the boiler. All the systems and operating properly at this time. Wrote down all model and serial numbers of the equipment. Charlie ask if there was a quieter bath fans the one under the mater suit is very loud and you can here it in the offices. Charlie also asked about thermostats I advised him to speak with his IT guys about them, he needs something g that will integrate in to the security system. The capacitors in both geos are weak and need to be replaced these should be under warranty. Need to order them and return to replace. The infloor problem was figured out before I got here they have a bad thermostat. Thanks Brad Replacement of the filters and water panels
Inducer motor assembly cracked and leaking -as evidenced by rusting in the inducer compartment Inducer motor using 1.5 amp draw and is rated for 1.3amp Oil coming out of inducer Blower motor did not start up during one of the test firings. System amp draw is irregular and â€”â€”- replace inducer and assemblyâ€”â€” â€”â€”- replace blower motor â€”â€” High x-air readings. And heat exchanger is Showing wear due to age System is about to be 18years old. Avg life 15. Serv tech did not charge for this call
No heat. Thermostat was blank. I found the fuse was blown after James replaced the electrostatic filter. I replaced the fuse and fixed some wiring. Cycled the furnace. Itâ€™s operating properly.
Water forming because the female receiver on the transition assembly has cracked and thatâ€™s where the water passes through to the condensation trap. 2017 system so it should be under warranty. Part number in photos Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Tune ups maintain warranty No money taken
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved