Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Dan did a.GREAT job for us.on all 5 furnaces. 😁👍
Always a pleasure to work with Black Hawk. Technician did a great job was thorough and explained all the details for me to understand what was done.
Hunter was very knowledgeable and was a very nice and friendly
Excellent service and comuunication
He arrived on time and was fast. He explained everything he did very well
I performed a cleaning on the furnace. The filter is clean. I cycled the zone system. Found the damper for zone 2 is failing and wonâ€™t always open all the way. I took a picture of the model of damper. This is could be causing the noise in the back of the house. The office will quote a price for the damper. The furnace is operating properly at this time.
Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Inspected heat exchanger Tested igniter Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec System working well at this time Now scheduling spring AC tune ups
Installed gas furnace
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Checked your condensate drain trap Furnace had blower Mtr replaced 3-21-17 gerondale hvac Possibly replaced hi limit switch - gerondale hvac Recommend HV wiring repair Recommend inducer motor replacement as itâ€™s using more power than designed and failure is expected Mark (joanns son, is landlord) H 920 9652815 C 920 6642557 1516 orchid lane Green Bay/ashwabbon wi 54313
System has rust debris all over it, rust is coming from heat exchanger Inspected heat exchanger massive amount of decay in 1 st past 2nd heat exchanger System working at this time Reading on flue were inconclusive Recommend second opinion Showed customer using snake camera the extent of the damage to the heat exchangers Dispatch fee charged
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved