Hunter was very knowledgeable and was a very nice and friendly
Excellent service and comuunication
He arrived on time and was fast. He explained everything he did very well
I truly liked the "I'm on my Way" text message showing a pic of the service tech and the short bio...I've not seen this before but I enjoyed the information. Tech was on-time, efficient and provided a full update and invoice before leaving, can't really get much better than that...
Main area not working very well tstat is calling for heat but not heating up enough. Radiators are cold so I purged the air out of them and increase the speed on the pump. This will increase flow before it was 2 gpm now its 4 gpm. Boiler system is operating properly at this time. Thanks Brad
Furnace clean and tune. Cycled system. Ch3cked heat exchanger, ok. Checked, removed, and cleaned burners and flame sensor. Both were ok. Checked and tightened electrical connections and clamps. Found clamp loose which was causing some minor leaking leading to some rust buildup on bottom of burner compartment. Found a few wires loose. Clamped and tightened those up. Checked and cleared drain lines. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test. Exhaust numbers were normal. No CO found in airstream. Found some vibration from blower motor. Bearings sound ok. Blower wheel was dirty and this may cause some pitch vibration. Cleaned the wheel as best I could. Without higher end electronic air filtration, this dirt will return. System was very dirty. Recommend yearly maintenance to ensure best chance for longer efficient lifespan of unit. System operating normal at this time. Job complete.
Black-Haak is pleased to provide you with the electrical quote for your home. Included in this proposal is all of the necessary labor and materials to complete the project. Black-Haak will supply and install (2)100 AMP main electrical panel and (2) Exterior 100AMP overhead meter socket, all new pvc, wiring, and breakers. All of the existing electrical circuits in the home will connected to the correctly sized circuit breakers in the new panel. A new grounding electrical will be installed along with new electrical bonding. Any additional electrical items that do not pertain the electrical service change / replacement that the city inspector may find or want repaired will be given a separate estimate. The additional items are not included in the proposal. Black-Haak will conduct all of the coordination with the city and utility company. Please call Black Haak at 920-757-9990 to start the process of scheduling this appointment. Prices subject to change after 30 days.
Preformed Electrical Service Upgrade. Repaired all outside outlets. Eliminated all exposed wiring in attic. Installed electrical box for light in attic. Repaired all reversed polarity and ungrounded outlets. Repaired non working hallway light. Repaired/eliminated all visible violations in basement.
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter And replaced Inspected and tested inducer motor and blower motor Furnace working well at this time. Replaced thermostat batteries Please renew tuneups to maintain your warranty
Furnace clean and tune. Cycled system. Checked heat exchanger. Found heat exchanger very rusted and corroded with signs of cracks starting . Checked burners and ignition system, both are worn. Checked natural draft box and found some traces of CO in box. This system does not have a motor for exhaust and system is open to exhaust. This runs a high risk of CO leaking into the house with higher winds or blockage. No CO currently found in airstream. This system is very worn. High risk of failure. This system also lacks safeguards to ensure safe operation. Highly recommend second opinion for options. Job complete. Office to bill.
Customer stated that over the last three years, when he would run the heat and dishwasher, it would blow the breaker. Both the dishwasher and furnace are on the same 20amp breaker. This appears to be overloading the circuit. Called Joel and he quoted $175.00 plus tax to place them on different breakers.malso recommended a full electrical inspection of home to ensure no other issues are present. This service is 299.95 plus tax. I highly recommend this service due to current electrical issues. Safety check on furnace. Cycled. Heat exchanger is ok. Flame sensor and igniter are normal. Some rusting present due to crawl space location. No CO found in airstream. Normal levels of CO and XS air in exhaust. System operating normal at this time. Job complete.
Ac clean and tune. Checked indoor coil with refrigerant sniffer. Found indications of a leak on the coil. Checked and cleaned electrical compartment. Compressor and fan motor tested ok. Contactor is ok. Capacitor is original and worn. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. Indoor coil temp was 41, subcooling was 10, super heat was 9, indoor split was 18. Average life expectancy for this unit is 14 years. This system is 14 years old and worn. Cooling properly at this time. Job complete.
No cool. I opened up the electrical on the condenser. The contactor was pulled in. I tested high voltage on both sides, only had voltage on the incoming side. I pulled off one of the low voltage leads and reconnected it and everything ran like normal. I replaced the contactor that has pitted contacts and some mouse damage. The system is running normally.
The new air conditioner wasnâ€™t keeping up during the day. I cycled the air conditioner and checked the charge. Found the condenser coil was plugged with cottonwood. I washed the condenser coil. Checked the charge. It was low on charge. I added a pound of refrigerant to get the proper charge. I checked the split, it was at 19. Checked the air handler. Found the sensing bulb wasnâ€™t insulated. I insulted it. The air conditioner is cooling properly at this time. We need to come back to adjusted the lineset in the attic. Office will call to schedule that.
Customer stated that he had a no cool yesterday. TXV and service valves were frozen. Hooked up gauges and checked pressures and temps. Found coil temp low at 23 degrees. Filter is ok and no obstruction on evaporator coil. Added 1 pound 4 oz of R410-A refrigerant. High side went up, but suction side remained under freezing. Checked indoor coil and found half of the coil was freezing up and the upper half was warm. This indicates that there is a problem with the TXV not opening. Office will follow up with pricing for new TXV. warranty will be checked. Maintenance will be done after cooling issue is resolved. No payment collected at this time. System not cooling correctly at this time. Job complete.
Performed AC clean and tune, replaced 20x25x1 filter, inspected condenser electrical compartment and tested components capacitor and contactor both showing signs of age, sprayed condenser with coil cleaner, cycled the system on and checked pressures and temps system is slightly overcharged cooling at 24 degrees. This system is currently operating but due to age and condition future failure is expected. I am including a quote for repair as well as a quote for a package cleaning so we can ensure safe furnace operations this fall. Job complete
No cool on the geo system. Found the geo was tripped on a water flow error. I reset the unit. The geo turned on. I checked the pumps, they were running. Checked the pressure drop and temperature rise across the heat exchanger. Had 13 psi drop and a eight degree temp rise. This is ok. Checked a temperature split of the ductwork. Itâ€™s at 25 which is good. I tested the freeze protection thermistor and found itâ€™s not reading correctly and caused the unit to not run. We will order a new thermistor. The unit is cooling at this time Also found the zone board isnâ€™t allowing the geo to operate in 2nd stage. I jumpered out the board so it will run in second stage. We will quote a price to replace the zone board as well. Office will call with price for the zone board and the thermistor. .
Performed air conditioner start up. Used vacuum pump. Released the charge. Cycled the air conditioner and set the fan speed. Added 2 pounds of refrigerant to the unit. The air conditioner is running normally at this time.
Performed air conditioner clean and tune. Washed air conditioner, checked electrical components. Found the capacitor getting weak. Cycled the unit and checked the Freon charge. The unit is a little low on freon and starting to frost up. I performed a electronic leak search. Found the evaporator coil and the condenser coil is leaking Freon. The air conditioner is going to fail. Air conditioner is 22 years old. Eric has a home warranty, he will call to get a claim number and we will get replacement authorization on Monday. Office will be in contact with you.
Performed the level 2 AC cleaning. No leaks detected. Electrical components are starting to wear. Condenser coil has bent fins. Refrigerant charge tested good. Subcool was 15Â° with a 16Â° temp split. Unit is currently cooling properly at this time. However, due to age and condition, we cannot gaurante a long life expectancy.
Removed old boiler, water heater, and controls. Installed new IBC boiler indirect and controls. Filled and purged system, flushed with f5 cleaners and then added fluid filter. Preformed start up and everything is operating properly this time Will see a bill for the indirect and boiler upgrade. We will mail the focus on energy paperwork. Thanks Brad
Performed the level 2 AC cleaning. No leaks detected. Electrical components tested good. Capacitor tested in the required zone. Condenser was cleaned with water and nu brite. Refrigerant charge was normal. Subcool was 12Â° with a 17Â° temp split. Unit is cooling properly.
Boiler has been needing to get reset every day. I checked the boiler. The ignition module was on a 5 minute retry cycled. The pilot lit, the gas valve would get power but it wouldnâ€™t open. I reset the boiler and gas valve, cycled the boiler the burners lit now. The gas valve is getting stuck close after itâ€™s off for a while we will return with the gas valve and replace it.
Pulled a 3â€ liner down the chimney and conneced to the water heater.
Performed preferred client furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure. Took a temperature reading and set the fan speed. Performed furnace combustion test. The furnace is running normally at this time. Talked to the client about possibly getting the air conditioner checked out. The client will talk it over with his wife and call if they are interested.
installed new gas furnace and AC, all equipment tested and running start up complete on both units.
3-26-19. Removed old furnace. Installed new daikin 2 stage furnace. Installed metal to connect furnace to duct. Connected pvc to exhaust on furnace. Installed and setup t6 WiFi stat. Pulled new 6wire thermostat wire from upstairs to furnace. Reconnected gas piping and electrical wiring to furnace. Installed filter upgrade kit and new 213 filter. Ran new drain hose from coil and furnace to floor drain. Started furnace and everything running and draining properly. Thank you for choosing Black -Haak heating for your heating needs.
Installed new gas furnace and AC. Furnace is up and running and tested. AC has not been pumped down yet under pressure to cold.
Installed indoor air quality package with a 16x20x1 electronic air cleaner, a Aprilaire humidifier 600, and a PureAirX ultraviolet light. We cycled the system on to ensure operations. This system is currently operating normal at this time job complete
We are here to serve your Fox Valley home or business!Scedule a Service Today!
Copyright © 2019 | Black-Haak Heating, Inc | All Rights Reserved