Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
We’ve used Black-Haak for years and they never disappoint. Dan was kind, professional, and polite. Good man!
Kody was great! Very informative and helpful!
The technician was prompt and professional. Everything was explained in detail and exceeded my expectations.
Dan is a very nice man. Answers any questions.
Dan, did a great job of explaining everything to us. We are new home owners and he really took his time to help us get to know our HVAC system!
Service guys were very good
Seemed to be knowledgeable.
Hunter was courteous and efficient.
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked, removed, and cleaned burners and flame sensor. Both were very dirty and rusted. Cleaned as best as I could. Checked igniter, tested normal. Checked and tightened electrical connections and clamps. Cleared drain line. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test and slightly elevated levels of XS air were found . No CO found in airstream. System is operating normal at this time. Yearly maintenance is recommended to ensure proper operation. Job complete.
Adjusted inducer outlet clamp Tailored drain
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. No issues with the furnace at this time.
I performed the furnace start up. I changed the filter. I adjusted the gas pressure. The furnace is operating properly.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found all chambers are very rusted and corroded. No visible cracks found with camera, but several areas that will crack in future. Checked igniter and flame sensor, ok. Checked, removed, and cleaned burners. Ok. Checked and adjusted gas pressures to maximize efficiency efficiency. Preformed combustion test and found high levels of XS air in exhaust. No CO found in airstream. Found ventor motor bearings are worn and noisy. Average life expectancy for this unit is 14 years. This unit is 12 years old and has several parts that are showing signs of getting worn. Due to age, condition, and cost of repair, second opinion recommended for options. Job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved