Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Our technician Gary did a phenomenal job! He was very efficient and explained everything well to us. He had our furnace back up and running in a matter of minutes which was wonderful! Thank you so much!
Tec explained the word he did and answer all my questions very well
Great service, excellent technician.
The service started a couple of weeks ago and ultimately we have a working AC system and a new furnace; we are very pleased. The service, scheduling, promptness, courtesy, and workmanship have been excellent. We'd like to thank Anthony, Dan and Dan, Craig and Craig, Kory, Scott, and Tim. Let's not forget McKenzie and Andy with the scheduling and follow-up. Thanks again.
The Craig and Craig team worked very well; installation went well. Thermostat and furnace details/operation were explained carefully and thoroughly. Great workmanship. Arranged for chimney liner (for gas water heater) to be installed at a later date.
Hunter is prompt, courteous, and thorough. He answered all my questions and taught me a thing or two. The new fan checked out perfectly. He explained all the differences and answered questions about the service. Good man! It is an expensive motor, but it is absolutely necessary; I have no complaints.
I devlivered the new filter pads, I checked the filter, it was clean. I let the pads by the geo unit. I removed the bad ballast in the uv light. I installed the new ballast. I replaced the uv lights as well. Cycled the uv light, itâ€™s working properly now. The office will send a bill for the filter and uv light bulb. The ballast is under warranty.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found all chambers have some rusting and corrosion. No cracks found visibly. Checked, removed, and cleaned burners and flame sensor. Both ok. Found igniter to be getting worn. Whiting found on igniter surface, no cracks found at this time. Checked and tightened electrical connections and clamps. Cleared drain lines, no obstruction found in lines or pressure tubes. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test. Normal levels found in exhaust. No CO found in airstream. System showing some signs of getting worn, but system operating normal at this time. Job complete.
Performed furnace clean and tune. Found the water leak was caused by the rubber exhaust coupling not being installed properly. I fixed the coupling. The furnace is operating properly and safely.
No heat Dirty flame sensor Recommend cleaning Took payment for cleaning but did not complete cleaning
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked, removed, and cleaned burners and flame sensor. Both normal. Igniter tested normal. Checked and adjusted gas pressures to maximize efficiency. Checked and tightened electrical connections and clamps. Cleared drain lines. Preformed combustion test and found normal levels no CO found in airstream. System operating normal at this time. Job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved