Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Arrived on time, explain the services, etc
Hunter De Witt was very knowledgeable and friendly at the same time. His respect for my military service was admirable. A true asset to his company
Dan is not only good at what he does but he is even better at customer relations. I was very pleased with everything he did for our home
Black Haak has an outstanding workforce, all working in perfect coordination to get the job done quickly, efficiently, and correctly! They did an EXCELLANT job! Friendly, considerate, and courteous too...answering all questions, and very informative!
Rust in blower compartment Gas valve unstable. It varies the pressure from 3.45 to 3.54 wci while running. Recommend replacement part but (second opinion) part v replacement is preferable as the system is 20years old. X air is high at 132.2 Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Inspected heat exchanger Tested igniter Checked condensate trap Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec
Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Inspected heat exchanger Tested igniter Checked condensate trap Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec Leak checked indoor coil System working well at this time Now scheduling spring AC tune ups
Customer name is Taylor Jacobson No heat Inducer seized Inducer collector box is damaged and leaking Additionally there is rust on the circuit board And pressure switch needs replaced Please quote customer for 213 and spaceguard conversion kit. Part v replacement Second opinion with Dan Fox Dan to call @ 2 pm I did charge customer st dispatch fee
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked, removed, and cleaned burners and flame sensor. Both ok. Checked igniter, ok. Checked and tightened electrical connections and clamps. Clear drain lines. Checked and cleared pressure switch tubes. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test and found normal levels in exhaust. No CO found in airstream. System is currently operating normal at this time. Job complete.
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. The furnace is running at this time. Noticed that the furnace is vented with 4 inch single wall tin. Type b venting is recommended. Office to call the customer to see if they want it fixed.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved