Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Good guy you can keep him. Represented your company well
Answered questions and went over all options. Very informative and helpful. Thanks!
Great job! Appreciate ability to get the job done quickly.
Excellent job! Appreciate the quick service.
Very good experience, high knowledge of products and services. Overall great experience. And would recommend to anyone
Did a great job explaining my options, ordering and installing my air conditioner, in a very timely manner. Communication from start to finish was accurate and informative, very helpful in understanding my options. Air conditioner was installed and is working properly. A few years back you installed my furnace, very happy with both installations. Thank you!
Installed 3 receptacles, replaced 2 single pole switches.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 42Â°. Unit is heating properly.
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. The furnace is running at this time. Found that the inducer motor bearings are noisy. Recommend continuing to get cleanings to monitor the inducer motor.
Performed the level 2 furnace cleaning and replaced the gas valve. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 50Â°. Gas valve was replaced under full warranty. Unit is heating properly.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found some rusting found in all chambers. No visible cracks found with camera. Checked, removed, and cleaned burners and flame sensor. Burners were corroded and rusted. Cleaned as best as I could. Checked and adjusted gas pressures to maximize efficiency. Checked and tightened electrical connections and clamps. Cleared drain lines. Ventor motor bearings are ok at this time. Preformed combustion test. Normal levels of CO found in exhaust. High levels of XS air found. This is caused by blockage in secondarily heat exchanger. No CO found in airstream. Average life expectancy for this unit is 14 years. System is worn, but operating normal at this time. Future failure is expected. Job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved