Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Woke up to no heat. Black Haak responded and arrived within 45 minutes. Evan quickly determined the problem. Luckily we were under warranty and the necessary parts were replaced. Preventive parts also were replaced under warranty. Great job!
Absolutely fantastic!!! He was very helpful in explaining what he was doing and why he was doing it. He was very knowledgeable and he gave me great instructions for what I should look for going forward. Wonderful experience!
Thorough and complete inspection with great customer service
Nice , trustworthy, educated tech. Happy to leave him a great review !
fast, and friendly. He took his time to explain what he was gonna do and got right to work! So thankful for his expertise and for the heat ☺️
Performed AC clean and tune; inspected the electrical compartment and tested components capacitor did test weak, sprayed outdoor condenser with coil cleaner, cycled the system on to check pressures and temps while doing this the system completely shut off with the contactor disengage (no low voltage) I was able to bypass the thermostat to finish up checking pressures on the system. Will need to replace the capacitor in the near future. No cool need to revisit. Job complete
Findings Inducer motor tested at 4.9 amp max rating is 3.7amp System tripped on hi limit during tune up. Condensation at leak collector box Rusting in inducer box area X air Is 102.9 Flame sensor has rust on wiring attachment Inducer motor Collector box Flame sensor Hi limit switch All part recommend for replacement Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Inspected heat exchanger Tested igniter Checked condensate trap Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec Tested indoor coil. Dan Fox second opinion Now scheduling spring AC tune ups
Remove old boiler and install a new high efficiency boiler. Reuse old indirect tank and add a buffer tank in between the boiler and the zones. Install new boiler components and purge out the whole system. Prefom the start up. The new boiler is operating properly at this time and job is finished. Thanks Brad
Installed pressure switch Completed
Performed a preferred customer furnace start up. Checked over the furnace installation. Cycled the furnace. Set the furnace gas pressure and took a temperature rise. Performed a furnace combustion test. The furnace is running normally at this time.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved