Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Efficient, Fast and fair priced.
Gary was friendly and knowledgeable. He explained everything and was great.
I recently purchased a new home with features I was not familiar with. The technician went through them with me (i.e. Aprilaire system), so I can maintain them between calls.
Best service ever.
We have had Black-Haak Heating since 1984 because of their service and the employees they have working for them.
Technician was kind and courteous. Extremely knowledgeable. Respectful of our property. Would definitely recommend.
Friendly, knowledgeable technicians. Love our furance and how evenly warm our home is. Best decision we made when we needed to replace our old furnace.
Dan was great! On-time, great communication thru the process, and very knowledgeable. Highly recommend and very professional. Thank you!
Furnace start up. Cycled system. Checked electrical connections and clamps. Found ventor motor clamp installed incorrectly. Removed and installed correctly. Tightened connections. Checked incoming gas pressure. Checked and adjusted outgoing gas pressures to maximize efficiency. Checked and adjusted drain line. Preformed combustion test and normal levels found. Customer pointed out damage to vibration boot on supply trunk. This may have been caused from duct work moving due to install. Office to follow up for repair appointment. System operating normal at this time. Job complete.
No heat. Cycled system. Igniter would energize, flame would light, then system would drop out. Cycled several times with similar results. Removed burner box and gas manifold. Checked igniter, tested normal. Checked low voltage. Correct voltage. High voltage was tested. Correct voltage. Cleaned and checked flame sensor. Flame sensor was very corroded and dirty. Re installed burner box and flame sensor. Cycled system. System fired normal and continued to operate normal for over 15 mins. System is in major need of maintenance to help ensure proper operation. System operating normal at this time. Job complete.
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked, removed, and cleaned burners and flame sensor, both ok. Checked electrical connections and clamps, tightened . Cleared drain lines. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test and found normal levels in exhaust. No CO found in airstream. System operating normal at this time. Job complete.
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. No issues with the furnace at this time.
Furnace start up. Cycled system. Checked clamps. Checked adjusted gas pressures to maximize efficiency. Tightened electrical connections. Checked for sequence of operation. Preformed combustion test. No CO found in airstream. System operating normal at this time. Job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved