Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
Very satisfied with Jeremiah's service call. Courteous, friendly and very professional. Thanks Black-Haak...
Servicing tech was very professional, performed a thorough pre-season inspection and tune up on our furnace. Also was very friendly and helpful with our questions. Would recommend Black-Haak to anyone.
Furnace clean and tune, cycled system. Checked heat exchanger. Found some rusting and corrosion in heat exchanger. Checked, removed, and cleaned burners and flame sensor. Burners are rusted and corroded. Cleaned as best I could. Checked and adjusted gas pressures to maximize efficiency. Checked and tightened electrical connections and clamps. Cleared drain lines. Found areas of rust in burner compartment. Tightened clamp for drain line. No standing water found. Found major rusting in blower compartment as well. Preformed combustion test and found normal levels. No CO found in airstream. Replaced 201 filter with 213 filter and upgraded kit. System operating normal at this time. Average life of this unit is 14 years.
12/27/18. Installed aprilaire 600 humidifier. Ran thermostat wires from control to furnace. Installed outdoor sensor in fresh air intake pvc. Ran all new drain hose from humidifier and furnace to floor drain. Ran copper water line from hot water pipe to humidifier. Tested humidifier. No leaks. Thank you for choosing Black-Haak for your heating needs.
Performed level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 41 degrees. Unit is operating normally at this time. Thank you for choosing Black-Haak! Please take the time to complete our online
Prefom preferred customer geo cleaning and replace 213 filter. Wipe down and vacuum unit. Test electrical components. Capacitor starting to get weak and contactor pitted and burned. Customer didnâ€™t want to do anything this year but will prolly have them done next year. Used refigrent sniffer on unit no leaks found. Cycled unit and tested. 11.5 gpm 7 water deltaT 22 Air delta t. System operating properly at this time. Thanks Brad If you could take a few mins and fill out a survey on how I did today that would be greatly appreciated.
Performed furnace clean and tune; started by inspecting the exhaust and intake pvc ensuring all connections were secured, I then removed and cleaned burners along with the flame sensor, Next I cleared out the drain line, I then cycled the system on and checked gas pressures, lastly I performed a combustion test verifying no CO in the airstream. This system is currently operating normal at this time job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved