The coldest day my furnace decided to take a crap, Back Haak was quick to help replace mine.
We had the furnace put in our home w/ air conditioner as an option after some remodeling is to be done. This entails moving the present A/C unit and replacing this unit. The contractor said they would be handleling this phase of the remodel also. We wish to allow the contractor do the A/C work that is in the bid. Thank you for your option on the A/C unit but we will go with what is stated. We still will use your service in the future.
Black-Haak always provides excellent and friendly service as well as great communication; they call before arrival and follow up if a repair was necessary to ensure satisfaction.
Performed preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. The furnace is running normally at this time. Performed preferred customer air conditioning cleaning. Checked the indoor coil for leaks. Did not find a leak at this time. Cleaned the condenser unit. Checked the electrical. Cycled the air conditioner and checked the refrigerant levels. Found that the air conditioner is running low on 410a refrigerant. The customer would like to wait until spring and then have an air conditioner cleaning to recheck the pressures. Office to call in the spring to schedule the cleaning.
Ac clean and tune. Cleared drain line and checked filter. Checked indoor filter with refrigerant sniffer. Found a few spots that indicated that there may be a leak. Cycled system. Checked and cleaned electrical compartment. Checked compressor and fan motor. Both tested lower. Capacitor is ok. Contactor is worn and rusted. Used coil cleaner on condenser coil. Hooked up gauges and tested pressures and temps. While checking pressures, fan was very noisy and was slowing down due to very heavy bearing wear. Unable to get accurate readings due to very high head pressures from lack of airflow. Looks as though system is low on charge and fan needs to be replaced along with several other parts. System is very worn. Average life of this unit is 14 years. This system is 30 years old and in very poor condition. System may cool for short period of time, but major failure is expected. Second opinion is recommended. Job complete.
Performed furnace clean and tune. Installed new filters. Cycled the furnace, itâ€™s operating safely at this time.
Performed preferred customer air conditioning cleaning. Found no issues with the air conditioner at this time.
Furnace clean and tune, cycled system. Checked heat exchanger, found some rust, but no cracks at this time. Checked electrical system. Checked and adjusted gas pressures to maximize efficiency. Found drain trapped plugged. Removed and cleaned out trap. Water is now moving freely. Checked for levels of CO and XS air in exhaust, normal levels found. No CO found in airstream. System is operating normal at this time. Job complete.
Performed preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Cycled the furnace. Checked the motors for proper operation. Cleaned the drain trap. Performed furnace combustion test. The is running normally at this time. The customer was experiencing condensation on the ductwork near the fresh Air equalizer duct. Adjusted the balancing damper. They will see if that works. Also we were here to repair the exhaust vent on the water heater. The customer was wondering if we could do anything about the rust on the water heater and would like a call from Jeff.
Performed the start up on a new furnace. No gas leaks detected. Gas and exhaust levels are normal. No CO detected in the air. Venting and electrical components are properly installed. Drain is working. Heat rise was 41 degrees. High limit passed safety test. Unit is operating normally at this time. Thank you for choosing Black-Haak! Please take the time to complete our online
Performed level 2 furnace cleaning. Burners are clean. Flame sensor is wearing. Inducer motor bearings are starting to wear. Heat exchanger looks okay. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 44 degrees. Unit is operating normally at this time. Thank you for choosing Black-Haak! Please take the time to complete our online
Performed furnace clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, I then removed and cleaned the burners along with the flame sensor, as well as inspected the heat exchanger did find large amounts of rust did perform a powder test and did receive blowback from all 4 cells, cycled the system on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream, did ohm the igniter it did test wea, also replaced the 16x25x1 air filter. This system is currently operating normal but is showing signs of age. Second opinion scheduled with Rick 02/12/19 at 1pm Job complete
Installed new gas daikin furnace new t-4 stat new line voltage pulled back found splices in wire. New venting and gas line furnace conversion done. Everything up and running. Need to return with drop elbow.
Performed level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger is showing minor signs of wear. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 44*. Investigated the humidifier. It appears to be okay. Display shows 39%. Might not be kicking on due to the warmer and damp weather. Unit is operating normally at this time. Thank you for choosing Black-Haak! Please take the time to complete our online
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. The furnace is running normally at this time. Customer would like a call in the spring to schedule a possible air conditioning cleaning.
Checked power on breakers in breaker box. Checked power in office. Checked power for garage freezers. Replaced owner supplied fuse in fuse box in workshop. All power is back on.
I was here to replace the gas valve in the furnace. I set up the new gas valve to lp. I replaced the gas valve and wired it to the furnace. Cycled the furnace and set the gas pressures. I checked the temperature rise and itâ€™s at 55 which is good. Checked for gas leaks, found a leak and fixed the leak. The furnace is operating properly at this time. No charge, part is under warranty.
Was here for a boiler cleaning. Performed preferred customer boiler cleaning. Cycled the boiler the boiler would not fire up. Called Dan Fox. Dan sent out Jeremiah. Figured out that the flame sensor was touching to ground causing the boiler to see a flame. Readjusted the flame sensor. The boiler fired up. The boiler is running normally at this time. The customer is getting a free air conditioning cleaning. Office to call in the spring to schedule the air conditioning cleaning.
Performed start up on new Tempstar furnace. No gas leaks detected. Combustion analysis was normal. No CO detected in the air. Drain is working. Electrical and venting is properly installed. High limit passed safety test. Heat rise was 58 degrees. Unit is operating normally at this time.
I replaced the blower motor and the blower control board. I cycled the furnace. Itâ€™s operating properly at this time.
Performed furnace start up. No gas leaks detected. Combustion analysis test was normal. No CO detected in the airstream. Unit is operating normal at this time. Sold and installed a polarized electrostatic filter. I showed the customer how to safely and properly change the filters.
Installed Daikin Gas Furnace M#DM96VC080 S#1708268662 Removed the old furnace and installed a new gas furnace. Tied into the existing gas line and venting. Ran a new drain line. Installed a new thermostat. Customer paid $5,208.00 at this time for just furnace. When we return to do AC they will pay balance of $4,391.00. Will still need a tech start up. Thank you for choosing Black-Haak. Please take a moment to fill out our online survey.
Performed level 2 AC clean and tune. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is clean. Refrigerant charge was good. Unit is operating normal at this time.
Was here to replace the roof top unit filters. Replaced the roof top unit filters.
Performed level 2 AC clean and tune. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is cleaned out. Refrigerant charge was normal. Temp split was 17 degrees with a 12 degree subcool.
Performed level 2 package cleaning. Furnace. Cleaned flame sensor and burners. Wiped away any dust in blower and burner compartments. Inspected heat exchanger. Cleared drain hose. Combustion test was normal. No CO in airstream. AC. No leaks detected at indoor coil. Electrical components tested in the caution area. Refrigerant charge was normal. Temp split was 17 degrees. HVAC system is operating normal at this time.
I replaced the pressure/temperature gauge that was leaking water. Bleed the air out, system is operating as normal. System is under a year old, covered under company warranty.
I completed a level 2 preferred customer cleaning on the Tempstar furnace. The heat exchanger has mild rust. The igniter and flame sensor are both good. The gas pressures are good. The furnace is running safely. I changed the Aprilaire 213 filter media. I used my refrigerant leak detector on the indoor coil and found a couple leaks, the unit is older and it could be beneficial to hear some options on A/C equipment.
We are here to serve your Fox Valley home or business!Scedule a Service Today!
Copyright © 2019 | Black-Haak Heating, Inc | All Rights Reserved