Black-Haak Heating remains committed to taking care of our customers’ heating, cooling, air quality and electrical needs during this crisis. Our number one goal is to keep our customers and employees safe and we will continue to closely monitor guidelines and recommendations from the Centers for Disease Control. Read More
The coldest day my furnace decided to take a crap, Back Haak was quick to help replace mine.
We had the furnace put in our home w/ air conditioner as an option after some remodeling is to be done. This entails moving the present A/C unit and replacing this unit. The contractor said they would be handleling this phase of the remodel also. We wish to allow the contractor do the A/C work that is in the bid. Thank you for your option on the A/C unit but we will go with what is stated. We still will use your service in the future.
Black-Haak always provides excellent and friendly service as well as great communication; they call before arrival and follow up if a repair was necessary to ensure satisfaction.
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. No issues with the furnace at this time.
Completed installation of a 1/2â€ gas line for the future gas stove. Connected the new Flashshield gas line to an existing tee in the main gas line of the house. Routed the Flashshield to the hole in the bottom of the wall behind stove, and terminated it into a recessed wall box designed for gas appliance hook ups. Used the leak detector to check for leaks and found none. Thank you for choosing Black-Haak Heating and Electric. Please take a moment to fill out our online survey.
Small leak detected below collector box. Recommend replacement gasket Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Checked condensate trap Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec System working well at this time Now scheduling spring AC tune ups
Performed a preferred customer furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure and checked the fan speed. Performed a furnace combustion test. The furnace is running normally at this time.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found some rust and corrosion. No cracks found. Checked, removed, and cleaned burners and flame sensor. Both ok. Checked and tightened electrical connections and clamps. Cleared drain line. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test and found normal levels in exhaust. No CO found in airstream. System operating normal at this time. Job complete.
We are here to serve your Fox Valley home or business!Schedule a Service Today!
Copyright © 2020 | Black-Haak Heating, Inc | All Rights Reserved